Click on the image below to rotate in 3-D
|Size of Conductors:||8 GA or smaller|
|Maximum # of Conductors:||Up to 50. See NFPA70 : NEC Article 376.21|
|Cross-Sectional Area of Wire Tray:||4 in2|
|Ampacity Adjustment Factor Calculations::||Per NEC 376.22 (B), adjustment factors in 310.15(B)(2) shall be applied only where the number of current carrying conductors exceeds 30. When calculating adjustment factors per NEC 310.15(B)(2)(c) note the Wire Tray is typically 1-3 in. off the surface of the roof.|
|Compliant with Specifications:||NFPA70 : NEC Article 376.21
The SunLink RMS integrated wire management solution will help you achieve new levels of installation efficiency. Customers who have used this solution report saving an average of 40% in on-roof time compared with other wire management strategies.
Can also be used as a ventilated cable tray compliant with NFPA70 : NEC Article 392.